We try to always offer you the lowest prices possible, but some manufacturers require that we only show these low prices once you take further action. To see the price, simply add the item to your cart or sign in. Add item to cart for lowest price. Please check the box below to confirm you are aware that this item is for non-potable water applications only. This product will NOT be used in the installation or repair of a potable water human consumption application. You must agree to this statement in order to purchase this product.
|Published (Last):||13 October 2007|
|PDF File Size:||17.6 Mb|
|ePub File Size:||5.73 Mb|
|Price:||Free* [*Free Regsitration Required]|
International Sales and Service Offices in all principal cities of the world. Power Dissipation: EC 10W maximum. M Fig. Read these instructions carefully.
Failure to follow them Install the EC or RM where the relative humidity could damage the product or cause a hazardous never reaches the saturation point. The EC or RM condition. Maximum wire lengths: earth ground terminal that must be grounded to For the EC or RM, the maximum length the metal control panel with wire as short as of leadwire to the terminal inputs is feet practical.
Disconnect the power supply before beginning installation to prevent electrical shock and equipment Mounting RM damage. More than one disconnect may be involved. Dust Cover mounting. Wall or burner installation. Flame signal amplifier mounting. ST Purge Card installation. For each test, open the master switch and install the Equipment Recommended jumper wire s between the subbase wiring terminals 1. Site Configurable Jumper Options. Flame Signal. LED, make sure the automatic main fuel valve is open; This check applies for gas and oil burners that do not use a Shut down the system by lowering the set point of pilot.
Keep the warmup period. A decrease in signal strength as the pilot gas pressure just above the reading noted in refractory heats up indicates hot refractory saturation. Page All Installations Automatic pilot valve s should be energized but 0. Safety shutdown occurs. Failure to ignite main. Each of the six lockout files retains the Sequence And Status Hold Information.
NOTE: Normal sequences are in bold type, while abnormal sequences are not in bold type. This manual is also suitable for:.
Honeywell Thermostat RM7895A User Manual
Honeywell RM7895 Series Wiring Diagrams
Honeywell On-Off Primary Control With PrePurge RM7895A1014, Intermittent Pilot